REQUEST FOR PUBLIC COMMENTS
ON DRAFT AIR PERMIT
REGULATING THE EMISSIONS OF AIR POLLUTANTS
(Docket No. 07-CA-PA-08)
Pursuant to Hawaii Revised Statutes (HRS), Chapter 342B-13 and Hawaii Administrative Rules (HAR), Chapter 11-60.1, the Department of Health, State of Hawaii (DOH), is requesting public comments on the following DRAFT PERMIT presently under review for:
Covered Source Permit (CSP) No. 0317-02-C
Initial CSP Application No. 0317-04
Mauna Loa Macadamia Nut Corporation
Mauna Loa Macadamia Nut Plant
Biomass/Oil Fired Boilers and Diesel Engine Generators
Located at: 1 Macadamia Nut Road, Keaau, Hawaii
The DRAFT PERMIT is described as follows:
CSP No. 0317-02-C will grant conditional approval to operate an existing primary boiler fired on biomass (macadamia nut shells) or used oil, a back-up boiler as an additional unit that burns only biomass, and two existing diesel engine generators fired on fuel oil No. 2. The main boiler is equipped with an electrostatic precipitator for controlling particulate emissions. Both the main and back-up boilers are subject to the state particulate emissions limit for biomass boilers requiring emissions not to exceed 0.4 pound of particulate per 100 pounds of biomass burned. Modifications to the facility include an allowance to burn macadamia nut shells continuously in any one boiler. The macadamia nut shell fuel consumption is currently restricted to 12,000 tons per year (TPY). Also proposed, is an increase in the used oil fuel consumption for the main boiler from 270,000 gallons per year to 350,000 gallons per year. This permit, if approved, will supersede Noncovered Source Permit (NSP) No. 0317-01-N, issued on December 20, 2002 under application 0317-02, in its entirety. Changes to the facility will increase emissions as follows:
Pollutant Boiler Emissions (TPY) Significant Level
Biomass Fuel Used Oil Fuel Total Emission (TPY)
Consumption Change Consumption Change Change
SO2 1.2 see note a 8.6 see note b 9.8 40
NOX 17.5 see note c —— 17.5 40
CO 28.1 see note c —— 28.1 100
VOC 0.61 see note c —— 0.61 40
PM 14.2 see note c —— 14.2 25
PM10 10.5 see note c —— 10.5 15
a: Based on remaining capacity to burn macadamia nut shells above the previous 12,000 TPY limit for the main boiler after burning 350,000 gallons per year of used oil.
b: Based on burning 350,000 gallons per year of used oil in the main boiler as worst-case.
c: Based on continuous firing of macadamia nut shells in the main boiler as worst-case.
The ADMINISTRATIVE RECORD, consisting of the APPLICATION and non-confidential supporting materials from the applicant, the permit review summary, and the DRAFT PERMIT, is available for public inspection during regular office hours, Monday through Friday, 7:45 a.m. to 4:15 p.m., at the following locations:
Clean Air Branch, Department of Health
919 Ala Moana Boulevard, Room 203, Honolulu, Oahu 96814
Hawaii District Health Office, Department of Health
1582 Kamehameha Avenue, Hilo, Hawaii
Sanitation Branch, Keakealani Building, Department of Health
79-1020 Haukapila Street, Room 115, Kealakekua, Hawaii
All comments on the draft permit and any request for a public hearing must be in writing, addressed to the Clean Air Branch at the above address on Oahu and must be postmarked or received by June 8, 2007.
Any person may request a public hearing by submitting a written request that explains the party\u2019s interest and the reasons why a hearing is warranted. At the sole discretion of the Director of Health, DOH may hold a public hearing if a hearing would aid in DOHs decision. If a public hearing is warranted, a public notice for the hearing will be published at least thirty days in advance of the hearing.
Interested persons may obtain copies of the administrative record or parts thereof by paying five cents per page copying costs. Please send written requests to the Oahu office of the CIean Air Branch listed above or call Mr. Michael Madsen at the Clean Air Branch in Honolulu at (808) 586-4200.
Comments on the draft permit should address, but need not be limited to, the permit conditions and the facilitys compliance with federal and state air pollution laws, including: (1) the National and State Ambient Air Quality Standards; and (2) HRS, Chapter 342B and HAR, Chapter 11-60.1.
DOH will make a final decision on the permit after considering all comments and will send notice of the final decision to each person who has submitted comments or requested such notice.
Chiyome Leinaala Fukino, M.D.
(SB05529275 5/9/07) Director of Health
REQUEST FOR PUBLIC COMMENTS